


Dadabaev S. DEVELOPMENT OF MATHEMATICAL MODELS IRRIGATION PUMPING STATION FIRST LIFTIn this article, the object of study is the irrigation pumping station of the 1st ascent (ANS1) of Asht district Republic of Tajikistan. The design capacity of the ANS1 is 1.7712 million m^{3} of water per day, and in the machine hall ANS1 has 4 electric motor series VDS2325 / 6916 with total capacity of 32000 kW. Irrigation pumping stations due to large pumps consume huge amounts of electricity. These units are usually equipped with an uncontrollable drive that leads to additional costs. To solve this problem it is necessary to develop a mathematical model and analysis of ways of controlling electric pumps. In order to create a mathematical model of the pump station ANS1 first created a flow chart ANS1, which is shown in Figure 1. After the analysis of the technological processes of the pumping station was proposed mathematical description and the result is a block diagram that describes the processes of the object (Figure 2). In practice, the feed pump is regulated mainly by the following methods: changing the speed of the pump, by throttling pipe, and step control of bypass flow. From all the above methods is effective to regulate pump speed variation, i.e. the use of variable speed electric drives. Adjustable electric drives can save energy and increase the lifespan of the equipment. The studies developed a mathematical model and analyze ways to regulate pump units ANS1. The analysis showed that the introduction and use of variable speed drives has many advantages such as efficiency and economy. Estimated energy savings in pumping units in the implementation of the variable speed drive is about 15 to 25 %.Key words: irrigation pumping station, pumps, mathematical model, equations, methods of control, electric motors, electric drive, frequency converters, soft starters.
References:
1. Braslavsky I.Y., Ishmatov Z. Sh., Polyakov V.N. Energy saving asynchronous electric drive/By red. Braslavsky. — М.:ACADEMA, 2004. — 202 p.
2. Gorunov A.N. Study the effectiveness of the variable speed drive pumps of the first lift. Thesis for the degree of candidate of technical sciences. Moscow 2013.
3.Gorunov A.N. The interaction of the first lift pumping systems and water treatment facilities. // M:.VSTVodosnabzhenie i sanitarnayatekhnika.2010. №1. 2426, p.
4. Gorunov A.N."Technological features modes pumping stations of the first ascent to the treatment plants". "Novie technology" №6, Moscow 2010.
5. DadoboevSh.T. Promising ways to optimize the drive mode with fan character of the load. Material for 10 international scientific and practical conference "Bdeschiteizsledvaniya" — 2014.Volume 48.Technology. Sofia, 2014.
6.DadoboevSh.T. Review and assessment of ways to control pumping units. // M .:Electrooborudovanie: ekspluatatsia i remont.2013.№12. 2830 p.
7.DadoboevSh.T. Features of the mechanical characteristics of electric load with fan character .// M .: Electrooborudovanie: ekspluatatsia i remont.2013.№11. 2830 p.
8.Lazarev G.B. VFD pump and fan installations.Silovaia electronica. 2007. №3.
9. Leznov B.S. Energy savings in pumping units. — M.: Energoatomizdat, 1991. — 144 p.
10.Leznov B.S. Energy saving and adjustable drive in pump and blower units. — M.: Energoatomizdat, 2006. — 360 p.
About this article
Author:
Year: 2015


Editorinchief 
Sergey Aleksandrovich MIROSHNIKOV 

